What Were They Thinking?
May 03, 2010
A version of this article appears in the May/June 2010 issue of Home Energy Magazine.
What does the picture show? It shows heating ducts, drainpipes, and potable water pipes on the ceiling of a crawlspace. The crawlspace is ventilated to the outside through a pair of opposing foundation grates on either side of the side addition to allow for cross ventilation. The contractor/architect unfortunately delineated the thermal boundary at the main-floor floor cavity, orphaning water pipes and heating/cooling ducts. In fact, the furnace was in that unconditioned crawlspace, which is effectively outside! Adding insult to injury, the house had two identical side additions flanking the central heated basement in the middle. Both these crawlspaces were accessible through flimsy access doors that met municipal code for access. These areas suffered from massive heat loss in winter (“My humidifiers aren’t working,” she said), massive infusion of excess humidity in summer (both from the sweating clay crawlspace floor and open vents) and lots of condensation and mold issues!
Toronto, Ontario, Canada
- FIRST PAGE
- PREVIOUS PAGE
© Home Energy Magazine 2016, all rights reserved. For permission to reprint, please send an e-mail to firstname.lastname@example.org.
Enter your comments in the box below:
(Please note that all comments are subject to review prior to posting.)