The Energy Penalty of Poor Duct Design
Click here to read more articles about Heating
A version of this article appears in the March/April 2001
issue of Home Energy Magazine.
March 01, 2001
A home with a poor duct system can't be energy efficient no matter how tight or well-insulated it is.
My company, Energy Master Home Incorporated, recently renovated a duct system for an energy association officer who had tried to build a model energy-efficient home for himself and his family. He had taken pains to follow every recommendation of a well-known energy guru. His house was tight and well insulated-although not as well insulated as he thought-and there was little we could do to reduce his heating and cooling loads. But, his ducts were a different story. The ducts were delivering 1,493 CFM of conditioned air from a two-stage, 5-ton geothermal heat pump (when it was operating at high speed). Since 400 CFM are needed to effectively deliver each ton of cooling capacity, the ducts were essentially strangling the air conditioner. It was delivering only 80% of what it could produce. As it turned out, ACCA Manual J load for the house was 4 tons. As the ducts were delivering almost 4 tons of conditioned air, the customer and his family were not unduly uncomfortable. This situation presents an all-too-common dilemma for the whole-house auditor. Strangely, the inefficiency of the duct system was compensating for oversized equipment. ...
To read complete online articles, you need to sign up for an Online Subscription.
Once an order has been placed there is an automatic $10 processing fee that will be deducted with any cancellation.
The Home Energy Online articles are for personal use only and may not be printed for distribution. For permission to reprint, please send an e-mail to email@example.com.