Fast Checks for Refrigerant Charge?
Click here to read more articles about Archive
A version of this article appears in the May/June 2002
issue of Home Energy Magazine.
May 01, 2002
For A/C technicians, new options exist for testing refrigerant charge levels.
Air conditioning systems that aren’t correctly charged don’t work as efficiently or for as long as they otherwise would.Yet incorrectly charged A/C systems are more common than correctly charged ones.Tests of more than 4,000 residential cooling systems in California revealed that about 34% were undercharged, 28% were overcharged, and only 38% had the correct charge. Why aren’t A/C technicians fixing this pervasive problem? Because, until recently, the tests that have been available to check charge levels have often been misunderstood or poorly applied.That could be changing. Refrigerant undercharge and overcharge both reduce A/C performance. For example, laboratory testing of capillary tube-controlled equipment indicates that an undercharge of 15% reduces cooling equipment total capacity by 8%–22% and its energy efficiency ratio (EER) by 4%–6%.An overcharge of 10% reduces capacity by 1%–9% and EER by 4%–11%. Laboratory testing of orificecontrolled equipment reveals similar effects.An undercharge of 15% has been shown to reduce EER by 11%; a 15% overcharge by less than 2%.Thermostatic expansion valve (TXV) -controlled equipment is much less sensitive to deviations from the ...
To read complete online articles, you need to sign up for an Online Subscription.
Once an order has been placed there is an automatic $10 processing fee that will be deducted with any cancellation.
The Home Energy Online articles are for personal use only and may not be printed for distribution. For permission to reprint, please send an e-mail to firstname.lastname@example.org.